GE LB1A7 240 volt AC replacement coil for CL00A310T, CL01A310T, CL02A310T, CL25A300T and CL03A300T IEC rated 3 pole contactors and RL4RA22T, RL4RA31T and RL4RA40T 4 pole relays. Coil provides for top side (line) A1 and A2 connection along with bottom side (load) A2 coil connection and is easy installed. To replace the LB1A7 coil, you will need a flat head screwdriver to remove the black u-shaped locking tabs that are located on the line side (L1-L2-L3) and load side (T1-T2-T3) of the contactor. Once released, the top housing will come off revealing the coil, spring and armature that must be reinstalled correctly for the contactor to operate as intended.
GE offers a line of 3 pole IEC and UL rated contactors that range from 5 H.P. @ 460volt up to 80 H.P. and accessories such as 4 pole auxiliary contact blocks and overload relays are available. Each contactor has the option to be mounted on the DIN rail or screwed to the base plate a panel for easy installation. 1 base contact (normally open) comes standard and each GE contactor has screw termination for easy wiring.